The height of the UV must be selected taking into account the height of the module on which it will be installed. In the protected room, the UV nozzle must be located so that the distance from the nozzle to the ceiling of the room does not exceed 1.0 m.
It is necessary to make sure that the nozzle is higher than the equipment (cabinets, racks, racks, etc.) installed in the protected room.
UV should not be used in rooms where a multi-tiered arrangement of nozzles is possible. When installing the outlet device, it is necessary to comply with the requirements for ensuring its reliable fastening to the module and the wall.